As we’ve moved our event dates to August 24-27, please note our Agenda will be updated frequently as we work with our speakers and panelists to schedule the best program possible for you. We appreciate your support and patience.
View, browse and sort the ever-growing list of sessions by pass type, track, and session type. With this Session Scheduler, you can build your schedule in advance and access it during the show via export or with the Mobile App, once live approximately 1 month prior to the event. For your schedule to sync properly with the mobile app, be sure to login to Schedule Builder.Agenda at a Glance
Stephen Spinazzola (Senior Project Manager, BALA|SVA)
Date: Thursday, August 27
Time: 1:30pm - 2:30pm
Pass Type : All Access, Standard
Track : Mission Critical Facilities & Energy Management
Session Type: Session
Vault Recording: TBD
The design relates to a chiller assisted cooling chilled water plant for data centers. In the system and method of the design, a fluid cooler is utilized as the primary means of heat rejection of the chilled water exiting the IT environment in the data center. After passing through the fluid cooler, if the design chilled water supply is above the set point, the water is passed through the water chiller where it is cooled before being pumped back to the IT environment in the data center. The use of a fluid cooler as the primary means of heat rejection of the chilled water allows for a reduction in the size of the chiller plant and emergency power plant sized by 35% which also provides lower initial cost and fuel consumption during emergency operations. Initial reduced construction costs are also attributable to a reduction in pipe and insulation material, and less copper for emergency power distribution. The operational EUE is approximately 1.1.